KNX ENO 630
The unit KNX ENO 630 serves as a unidirectional gateway between EnOcean radio devices and the KNX/EIB bus. With this device, commands and measured values of EnOcean wireless sensors can be transferred to the KNX bus, for example, to control KNX actuators.
For EnOcean sensors the device is based on the so-called EnOcean Equipment Profiles (EEP). The implemented profiles mostly are specified in the data sheets of the sensors. For the control of EnOcean actuators corresponding EEPs are emulated.
This means, the gateway sends radio telegrams such as a push button or a window contact. In addition the gateway supports logical and control functions and has a radio repeater included.
Broad variety of functions
The KNX ENO 630 is organized in 16 channels. Each channel can be assigned to one of the following functions.
Link from EnOcean sensor to KNX:
- Switching and contact functions
- Shutter up/down
- Window contacts
- Window handles
- Key cards switches
- Ressure switches
- Temperature sensors
- Humidity sensors
- Light sensors
- Presence sensors
- Gas sensors
- Room control devices
- Automated counter devices
- Environmental sensors (weather station)
- Digital inputs
Control / logic:
- Tracking circuit
- Lighting control
- Logical functions
- Gates (e.g. AND, OR, XOR)
The configuration of the device and the channels is done using the ETS software via the KNX bus. For the teach-in of the wireless components the keys and the display in the device are used.
Mounting and connection
The mounting can be done on a wall surface (e.g. brick-work or wood). The mounting holes match for a 55 mm flush-mounted box. The power supply of the device is realized via the bus.
The repeater function is used for extend distances between sensors and actuators. The KNX ENO 630 is a so-called level-1 radio repeater.
Bus monitor function
The integrated bus monitor function is used for system diagnostics directly on the device. The device can display both EnOcean telegram as well as KNX telegrams.
Configuration: KNX ENO Tool
The KNX ENO Tool software can be used to configure the Links between various EnOcean-Sensors and the KNX/EIB EnOcean-Gateway KNX ENO 626/630/632/6347636. The device configuration of the Gateway can be read, modified, exported and saved back to either the same or another Gateway. EnOcean Bus Monitor showing the EnOcean Telegrams send over the KNX Bus.
- Housing: plastic, white
- Surface mounting, matches on 55 mm flush-mounted box
- Dimensions: 81 x 81 x 25 mm
- KNX Bus approx. 12 mA
- Connector for KNX Bus (red / black)
- EnOcean, ISM Band 868,3 MHz, ASK
- Output power: 3dBm